Port Aransas Cooling Services
Whether you need to repair your air conditioner or install new air ducts, call Triple A Air Conditioning & Heating for residential Port Aransas cooling services.
Texas summers can be scorching. Fortunately, having access to a licensed, reliable AC contractor can help you face the brutal heat comfortably. We’re a family-owned HVAC company that puts quality services first.
At Triple A Air Conditioning & Heating, our team of experienced, highly skilled contractors has years of experience providing professional central AC repair, replacement, and maintenance services.
Have a look at our customer reviews and learn why more and more homeowners are making us their go-to cooling services provider.
AC Installation & Replacement in Port Aransas, Texas
Are you ready to install a new AC? Call us for quality air conditioning installation services.
When we arrive, we’ll evaluate your duct layout and discuss your cooling needs. Our friendly, professional team will guide you through the process of picking the right AC unit for your home, recommending options that will meet your needs and budget.
Do you already have an air conditioner but are dissatisfied with its performance? Speak with us today for quality AC replacement services. You might need to replace your air conditioner if it is more than ten years old, breaks down frequently, or has caused your energy bills to spike.
Our team will provide you with a new unit that is more energy-efficient and powerful, helping you enjoy enhanced cooling.
Ductless Mini-Split Services in Any Town on Mustang Island, TX
We also offer ductless mini-split installations, repairs, and replacements in Port Aransas.
There are several reasons why homeowners are making the switch to ductless AC systems, including:
- Quick installation: Since these systems do not require ductwork, installing them is quick and easy.
- Improved indoor air quality: Ducts often harbor dust, dirt, and allergens that can pollute your indoor air. Fortunately, with a ductless mini-split system, you won’t have to worry about dirty ducts.
- Energy efficiency: By allowing you to switch off units in the rooms you are not using, ductless systems help you lower your utility bill.
- Easy maintenance: Ductless mini-split systems are easier to maintain than central AC systems.
Are you looking to install a ductless AC in your home? Do you have a mini-split unit in need of professional repair? Call us for Port Aransas cooling services.
Contact us today to discuss your air conditioning needs with our friendly team!
Nueces County AC Repair & Maintenance
Even the most reliable air conditioning unit needs repairs from time to time to fix refrigerant leaks, faulty thermostats, and condenser coil issues.
With AC maintenance services, you can keep your unit optimal, extend its longevity, and help reduce the need for costly repairs.
During the AC tune-up, we will clean and inspect your unit’s components and repair any issues we find, safeguarding your AC’s functionality. You can make AC maintenance even more convenient with our membership plan! For $14.95 a month, you get two maintenance visits a year, priority scheduling, a 5% discount on new system installs, and a 10% discount on repairs.
for Port Aransas, TX
Very good company
Allen - Port Aransas, TX 78373
Daitchoin B. was on time, knowledgeable, courteous, and had excellent communication skills. The scheduling staff we had contact with was also excellent. First time to use Triple A AC/heating but would definitely use them again.
Excellent Service and Technician
Tony - Port Aransas, TX 78373
Daitchoin was very professional- he reviewed all the services and shared pictures of each thing he checked up on. This is a second visit from this same technician and I highly recommend him.
Steve - Port Aransas, TX 78373
Very professional and knowledgeable.
On arrival customer showed me return where water was dripping I found pvc drain line not glued and basically off inside of flex and dripping the water I also noticed around air handler not sealed…in return it’s soaking wet needs to be redone flooring as well is damaged customer advised me to just repair drain line for now in which I did customer is paid in full Note customer did not want to save card on file for ppm billing
On arrival customer stated all has been working great started off at left side of house airhandler smaller unit verified heating is working up to specs blower motor and capacitor both good ductwork inside is in horrible shape a lot of biological growth I cleared drain line me the out system into ac mode split was fair me pressures seemed did notice superheat fluctuation but it stopped free while me went back to normal told customer we would keep a eye on it amp draw at compressor and fan motor both well up to specs me capacitor reading within its percentile bigger unit right side of house system in heat mode found system performing well up to specs brand new system blower motor nice and clean as well as evaporator coil cleared drain line and turned system into cool mode found split to be excellent and pressures at outdoor condenser were spot on amp draw at compressor and fan motor both performing well and capacitor is reading within its recommended percentile ductwork for this system
Upon arrival, turn system to hitting mode recorded, inducer fan motor, making a very loud, humming noise. Check amp draw, pulled off, inducer fan motor and determined the inside fan blades were very rusted and corroded. Recommended changing inducer fan motor. Called Aces to confirm part was under manufacture warranty. Part is under warranty and will be shipped UPS ground and will call us as soon as it arrives in one to two business days. Customer would also like us to do a heating check up when installing the inducer fan motor. Customer paid in full for labor. .
Thermostat install and system assessment service call 2005 RUUD Air handler, 2012 Payne 2 ton condenser closet Replaced customer provided thermostat. Inspected system. Tested heating operation. All 5kw heating operations good at time of service, drawing 20 amps. Noted blower motor overamping rated not to exceed 1.3A reading at 1.56A. Highly recommend replacing motor before complete failure. Also noted evaporator coil is clogged and corroded. Needs a cleaning but do not necessarily recommend due to age and condition. Tested cooling operation. Noted condenser fan motor is leaking and nearing maximum amperage draw, reading at .46A rated not to exceed .5A. Recommend replacing before failure. Failed 35/5 mfd capacitor reading at 28/1mfd highly recommend replacing. Rusted contactor. Condenser coil is severely corroded compromising the efficiency of the system, elevating the operating temperatures and pressure, increasing the likelihood of the system leaking. Added service caps to the serv
System Running without signal service 2014 Trane 4 ton system attic -System running without being called to run - Foamed the attic Troubleshot system. Found the thermostat was set at 75° and it was 68° at time of service. Cooling was operating even though system was 7° colder than actual setpoint. Found that there is intermittent issues between the downstairs thermostat and the zoning board. Customer did inform me that they have power surges and outages regularly, I highly recommend replacing both of these components, and adding surge protection, to protect, and prevent this from reoccurring. Also noted, severe mold and mildew growth on the exterior and interior of the air handler cabinet and duct system with mold, now showing on supply grills. I highly recommend cleaning, treating and adding an air purification system, to prevent the reoccurrence and spread of the growth throughout the home. Foamed attic should now be a condition space to prevent the mold and mildew growth on the
Get in touch with Triple A Air Conditioning & Heating at 361-991-0967 to discuss your needs and schedule professional cooling services in Port Aransas, TX.