Robstown Cooling Services
Your AC unit is one of the most crucial appliances in your home. Whether you have a broken unit that needs repair or plan to install a new cooling system, trust Triple A Air Conditioning & Heating for all your cooling needs.
We proudly serve Robstown, TX, and surrounding areas. As a BBB-accredited, family-owned AC contractor, we believe in honest service and straightforward pricing. Customer satisfaction matters to us, so we go the extra mile to deliver high-quality solutions backed by a satisfaction guarantee.
Contact our trusted technicians for attention to detail and clean services.
Check out our stellar reviews from customers throughout the Southeast Texas region.
Robstown, Texas, AC Repair and Maintenance
Like any other appliance, your cooling system needs regular maintenance to work seamlessly. Proper AC maintenance also extends the life of your equipment and lowers energy costs. However, even the most well-maintained system needs repairs from time to time.
Contact us for central AC repair if you notice any of the following issues:
- Insufficient airflow
- High humidity levels
- Frequent cycling
- Warm air coming from the vents
- Water leaks
- Foul odors
- Unusual noises
With over 40 years of experience providing Robstown cooling services, we can get to the root cause of the problem and recommend the best solution. We also provide AC tune-up and AC maintenance services. Contact us for fast service and dependable solutions.
AC installation and Replacement in Nueces County
Nothing lasts forever. If your cooling system passes the ten-year mark, start budgeting for a replacement. However, the lifespan of your unit depends on several factors, including where you live and the type of unit you have installed. The best way to determine whether to repair or replace your AC system is to hire an expert to inspect your system.
If, after a thorough inspection, our team determines that an AC replacement serves your best interests, we can recommend a suitable unit and install it professionally according to manufacturer requirements.
A proper air conditioning installation goes a long way toward ensuring your system works as it should and delivers maximum value for money.
Ask about our membership plan and join to enjoy benefits such as priority scheduling, maintenance visits, exclusive discounts, and much more.
Ductless Mini-Split Services in a Western Suburb of Corpus Christi, TX
When a central air conditioner is not an option for your home or additional room, you can count on a mini-split cooling system to help you stay comfortable. These systems need no ductwork to cool or heat your space, and they provide zoned comfort.
At Triple A Air Conditioning & Heating, we offer full-service ductless mini-split solutions throughout Southeast Texas. Our trusted technicians handle everything from ductless mini-split installation and replacements to repairs and maintenance. Contact us for free estimates and the best warranties in the area.
for Robstown, TX
Robert - Robstown, TX 78380
Mike was very professional, he did an amazing job on our half split. I would highly recommend Triple A Air Conditioning & Heating
Response from Triple A Air Conditioning & Heating:
Thank you for sharing your experience with Triple A and our team Robert!
Robinson - Robstown, TX 78380
Beatrice - Robstown, TX 78380
Very informative and knowledgeable
Response from Triple A Air Conditioning & Heating:
Thank you for the positive feedback Beatrice!
No cooling; mini split: - Found mini split system not cooling due to being almost completely flat on refrigerant. When system was operating in cooling mode pressures were only reading 26 psi. I released the charge and pressure tested system using dry nitrogen to try and identify the leak. Leak searched system using soapy bubbles on indoor and outdoor coils along with the flare fittings at outdoor unit. I was not able to identify any leaks at this time. Recommended recharging the system and doing a dye test to pin point where the leak is coming from. Customers informed me that they are on a fixed income and can only afford so much. I did not charge anything additional for searching for the leak or pulling a vacuum on system. Quoted a price of $442 for service fee and 4 lbs of refrigerant. Customers did approve of doing so. - Vacuumed pulled down to 726 microns. Recharged system using 4 lbs 8 oz of refrigerant. System is now online and operational cooling with a 19 degree split. Befor
Not cooling; 2 ton system: - 2 systems household. The one not working today is the 2 ton. Found system not cooling due to having a restriction at the txv. Also noticed system is lacking an emergency disconnect at the outdoor unit. Had to kill power from the main panel that wasn’t labeled at all. Once I found the correct breaker, I labeled it 2 ton condenser. Also noticed that the drain line at the indoor unit is not insulated and is also lacking it’s designated p-trap and ss1 float switch. Got the approval for the immediate repair option which was replacing the txv. - Got the txv replaced. Also installed new liquid line filter drier as well. All welds and flares have been leak checked using nitrogen and soapy bubbles. Vacuumed system down to 730 microns. Tested cooling operations. System was cooling with a 20 degree split after topping it off with about 1.5 lbs of r-410a. Service panel has been cleaned out of all dirt and debris. Filter is clean. Wiped down air handler cabinet. System
Completed maintenance, summer and spring check with drain line flush.
Water Leak Service Call at the Lopez properties
Water Leak Service Call Troubleshot mini split system. Found that primary drain line was clogged. Filters dirty. Customer approved repairs. Flushed primary drain line, rinsed filters and sprayed coil with foaming cleaner. All system operations good at time of service. Customer also in mini split for master bedroom in apartment behind home. Room is a 16 x 10 pictures of electrical set up and mounting wall. Interior and exterior are included in the attachments.
Trust our experts at Triple A Air Conditioning & Heating to provide the first-rate Robstown cooling services you need. Call 361-991-0967 to discuss your needs and schedule service in Robstown, TX, or nearby areas like Rockport and Port Aransas.